Environmental Health and Safety
In accordance with New York State Sanitary Code requirement (Subpart 4-1, Protection Against Legionella), Suffolk County Community College tested a cooling tower located on the roof of the Health Sports and Education Center on the Michael J. Grant Campus, Brentwood, NY. The sample result reported on August 29, 2016 showed that the concentration of Legionella bacteria in the cooling tower was 2,140 colony forming units per milliliter (CFU/ml). Per NYS protocol, any result over 1000 CFU/mL requires public notification, review of cooling tower treatment protocols and online decontamination of the cooling tower. This notice is the required public notification.
As required by Subpart 4-1, the College performed an online decontamination procedure of the cooling tower on August 30, 2016, reviewed its cooling tower treatment protocols, and retested the cooling tower.
Lab test results for the retesting of the cooling tower were 3 CFU/ml. As per NYS regulations for test results less than 20 CFU/ml, no further action is required at this time.
If you have any questions regarding this incident, please feel free to contact Drew Biondo, Director of Communications, Suffolk County Community College, at (631) 451-4776 for additional information.
If you have any questions regarding Legionella, please refer to Suffolk County Department of Health Services website:http://www.suffolkcountyny.gov/Departments/HealthServices/HealthBulletins/LegionnairesDisease.aspx
At Suffolk County Community College, the safety of our students, staff and visitors is our paramount concern. To that end we are posting on this webpage our Health and Safety plans, as well as information and links concerning important safety issues. We will post more information as further health and safety issues come to light.
Philip Sandusky, Assistant Director of Public Safety and Environmental Health